Pipe Portal with C-412 Cap
- Furnish and install the Portals Plus Pipe Portal System at all points where up to four pipes 1" - 2" in diameter penetrate the roof.
- The Pipe Portal shall include an 18 gauge galvanized roof curb model RC-___A with integral base plate, continuously welded corner seams, factory-installed wood nailer, and 1.5" 3lb. rigid ï¬berglass insulation.
- The Pipe Portal shall be furnished with a laminated, acrylic coated, ABS plastic curb cover with prepunched holes and molded sealing ring on an 8" collared opening.
- An EPDM (Ethylene Propylene Diene Monomer) compression molded cap model C-412 shall be utilized.
- All Caps shall include Portals Plus' stainless steel Snaplock Clamps.
- Attachment and installation of the Pipe Portal shall be done in accordance with Portals Plus' instructions and the rooï¬ng membrane manufacturer's recommendations.
|32025||SMALL COVER & CAP W/ C-412 BLACK CAP||5|