Pipe Portal with C-126 Cap
- Furnish and install the Portals Plus Pipe Portal System as manufactured by Portals Plus, Inc., at all points where one penetration 2" - 6" in diameter penetrates the roof.
- The Pipe Portal shall include an 18 gauge galvanized roof curb model RC-___A with integral base plate, continuously welded corner seams, factory-installed wood nailer, and 1.5" 3lb. rigid fiberglass insulation.
- The Pipe Portal shall be furnished with a laminated, acrylic coated, ABS plastic curb cover with prepunched holes and molded sealing ring on an 8" collared opening.
- An EPDM (Ethylene Propylene Diene Monomer) compression molded cap model C-126 shall be utilized.
- All Caps shall include Portals Plus' stainless steel Snaplock Clamp.
- Attachment and installation of the Pipe Portal shall be done in accordance with Portals Plus' instructions and the roofing membrane manufacturer's recommendations.